Baxi MainEco Combi and System 24 – 28 – 35 / 18 – 6. – 02 . always disconnect the boiler from the mains and close the main gas inlet. View and Download Baxi Main Combi 24 HE installation and service instructions manual online. Main Combi 24 HE Boiler pdf manual download. Listed below are all the manuals for Main. Just click on the model or the Gas council number and the manual will download at the bottom of the page. After you.
|Published (Last):||28 April 2013|
|PDF File Size:||14.81 Mb|
|ePub File Size:||5.25 Mb|
|Price:||Free* [*Free Regsitration Required]|
Remove the trap and bracket from the boiler. Undo the locknut securing the trap to the bracket.
This item will post to United Statesbut the seller hasn’t specified postage options. There are 3 items available. Please enter a number less than or equal to 3. Page 51 Press the reset button on the flue overheat thermostat.
Plastic Disc Carefully examine the diaphragm and replace it if there is any damage. Reassemble in reverse order.
FREE BOILER MANUALS
Using the screws previously removed secure the inlet adaptor to the top panel. Accepted, Eligibility for PayPal Credit is determined at checkout. Fit the electrodes to the new burner. Pump Wiring Cover Fig. The combustion box door insulation piece can be Rear Insulation replaced by carefully bending up the two retaining tabs. We accept payment by: Most purchases from business sellers are protected by the Consumer 224i Regulations which give you the right to cancel the purchase within 14 days after the day you receive the item.
Baxi Main Combi 24 HE Installation And Service Instructions Manual
Please contact us before buying to enable us to quote the delivery costs. Paypal immediate payment onlybank transfers and cash on collection. Secure the deflector to the terminal with screws provided.
Reassemble in reverse order of dismantling. Please enter up to 7 characters for the postcode.
BAXI MAIN COMBI 24 HE INSTALLATION AND SERVICE INSTRUCTIONS MANUAL Pdf Download.
The boiler will not operate and the integral timer if fitted will require resetting once the selector switch is turned to either the DHW or CH position. Back to home page. Unscrew the thermostat from the adaptor in the outlet elbow.
By pressing ‘print’ button you will print baxo current page. Complete the discharge pipework and route it to the outside discharge point. Service Record Service Record It is recommended that your heating system is serviced regularly and that the appropriate Service Interval Record is completed.
Contact the seller – opens in a new 42i or tab and request a postage method to your location. The Main Combi 24 HE is a fully automatic gas fired wall mounted condensing combination boiler. Contact your Water Distribution Company for advice on suitable devices.
This item may or may not be in its original packaging. Please Contact us prior to ordering so we can arrange a collection time. Don’t have an account? Table Of Contents Building Regulations. Hand over the Users Operating, Installation and Servicing Instructions, giving advice on the necessity of regular servicing.
See other items More Representative APR variable The item you’ve selected wasn’t added to your basket. Please check package before signing for delivery ,a signature means you have received the package in good condition and cannot make a claim against the courier. Servicing The Boiler 9. No part of this publication may be reproduced or transmitted in any form or by any means, or stored in any retrieval system of any nature including in any databasein each case whether Tighten the pressure test screw and refit the modulator to baxk valve.
BAXI MAIN 24I 24FI Service Manual download, schematics, eeprom, repair info for electronics experts
You’re covered by the eBay Money Back Guarantee if you receive an item that is not as described in the listing. This item will be sent through the Global Shipping Programme and includes international tracking. No additional import charges on delivery. Gas fired floor standing combination boiler with unvented hot water storage 48 pages. For Servicing Purposes heat exchanger. Page 41 Pump Setting Automatic Air 2. Skip to main content. Only a flue 24k with the Main Combi 24 HE can be used.
Page 38 Fit the electrodes to the new burner. Page 15 Connection may be via a fused double-pole isolator with a contact separation of at least 3mm in all poles and servicing the boiler and system controls only. Email to friends Share on Facebook – opens in a new window or tab Share on Twitter – opens in a bax window or tab Share on Pinterest – opens in a new window or tab Add to Watch list.
Email to friends Share on Facebook – opens in a new window or tab Share on Twitter – opens in a new window or tab Baxk on Pinterest – opens in a new window or tab. Watch gaxi is full. Postage cost can’t be calculated.
To print the manual completely, please, download it. Terms and conditions apply.